Freezing air below its dew point temperature and then remove condensed water. Through the operation of the compressor→the vent discharges high-temperature and high-pressure gases→enter the condenser for cooling→become low-temperature and high-pressure gases→closure by capillary→become low-temperature and low-pressure gases→evaporation related heat absorption through the evaporator →return to the compressor, and become low-temperature and low-pressure gases
Under the circumstance of normal startup→through the operation of fan→damp air is inhaled through the air intake→pass the evaporator→the evaporator absorbs the water in air to aluminum sheet→become dry air→heat dissipation through the condenser→blow out from air outlet
Core part of a rotary dehumidifier is a cellular runner. The runner is a compound of special ceramic fiber carrier and activated silica gel; both sides of the runner are divided by purpose-made sealing device into 2 zones---Treatment Area and Regenerative Area; when moist air goes through Treatment Area of the runner, water vapor of moist air is absorbed by activated silica gel, while dry air is sent to anther area by the fan; slowly rotating runner carries nearly saturated water vapor into Regenerative Area; in the Regenerative Area, water in the runner is desorbed by reversely injected high-temperature air, and discharged out of the room by the fan. In this way, the runner restores dehumidifying capability, and completes the regeneration process. As the runner rotates consistently, above dehumidification and regeneration go on and on, and the rotary dehumidifier maintains its continuous and stable dehumidifying state.
Feature: In the producing process, troubles caused by the moisture of the products are always puzzling mankind. In the cellular runner synchronized to the moisture absorption process of regeneration after the adsorbent dehydration processing, the recycling of solid adsorbent, the entire work can be continuous moisture. To overcome the static can not be a continuous solid adsorption refrigeration dehumidifier and dehumidifier condensation at low temperatures, low humidity circumstances powerless shortcomings. Can play in low temperature and humidity conditions, can be continuous and steady, large dehumidification capacity characteristics. Fuda company's rotary dehumidifier is made to apply this advanced technology development, with special features can not Homo habilis. Rotor-type dehumidifier, dehumidifier with other methods of comparison, has its own unique characteristics;
1.Easy to get the dry air with ultra-low humidity. Provide continuously dry air that dew-point below 6 ℃ with low cost but refrigerant dehumidifier can't do.
2.Running operation and maintenance Simple structure and drive devices.It can get dry air by the workof runner,regenerative heater and fan.Operation is very easy.In addition,it belong to dry desiccant type which don't need to add hygroscopic agent,easy maintenance,low costs to operate and maintain
3.Durability In clean air environments,the performance of runner will not decrease and degenerate and operate for many years . ·Full range of Machines From general-purpose standard to low humidity-dry air type.Our machines are suitable for a variety of different conditions.
4.Nuisanceless Green Machine Since taking active silica gel and molecular sieve as green hygroscopic agent,In the use of dehumidifiers,it's safe and environment protection,clean,no dust and corrosive effect,moreover, it can sterilize,specially useful for pharmaceutical,food,chemical and biological and other industries.
Types of dehumidification
1. refrigerant dehumidification Cool the temperature of the air below dew point,and then removed condensed water. Effective when the dew-point of the applying place above 8~10℃
2.Compression and dehumidfication. Compress and condense the humid air,then remove the condensed water. Effective for small places,but not suitable for larges places.
3.Solid desiccant adsorption. Use function of capillary to make water absorbed by solid hygroscopic agent and it also can reduce dew point,however,absorption area will become bigger with the device at the same time.
4.Absorption of liquid desiccant Absorb moisture with spray of lithium chloride solution. Dew point can be reduced to -20℃,but device is large and fluid must be replaced.
Make thin sheet impregnated hygroscopic the into honeycomb rotor for ventilation and dehumidification. Simple structure,after a special design ,the dew point can decline to-60℃